Published at Thursday, October 11th, 2018 - 13:55:29 PM. Floor. By john.
Metal whiskers Raised floors and other metal structures such as cable trays and ventilation ducts have caused many problems with zinc whiskers in the past, and likely are still present in many data centers. This happens when microscopic metallic filaments form on metals such as zinc or tin that protect many metal structures and electronic components from corrosion. Maintenance on a raised floor or installing of cable etc. can dislodge the whiskers, which enter the airflow and may short circuit server components or power supplies, sometimes through a high current metal vapor plasma arc. This phenomenon is not unique to data centers, and has also caused catastrophic failures of satellites and military hardware.
Telcordia GR-2930 Telcordia NEBS: Raised Floor Generic Requirements for Network and Data Centers, GR-2930 presents generic engineering requirements for raised floors that fall within the strict NEBS guidelines. There are many types of commercially available floors that offer a wide range of structural strength and loading capabilities, depending on component construction and the materials used. The general types of raised floors include stringer, stringerless, and structural platforms, all of which are discussed in detail in GR-2930.
Any content, trademark’s, or other material that might be found on the PapihillsTour.com website that is not PapihillsTour.com’s property remains the copyright of its respective owner/s. In no way does PapihillsTour.com claim ownership or responsibility for such items, and you should seek legal consent for any use of such materials from its owner.